Zulkik The electro-mechanical controller is not as versatile as the NXT controller but has been a very reliable controller. Fleck commercial valves have been the standard valve in the water treatment industry for many years. Fleck manufacturers residential valves as well. They have the ability to operate on many different sizes of pressure vessel and can backwash up to a 63 inch diameter water softener. The valve has a Cv of 6. The Fleck commercial valve is a 2 inch valve, with a 2 inch inlet and outlet as well as a 1.
|Published (Last):||4 May 2014|
|PDF File Size:||20.83 Mb|
|ePub File Size:||8.75 Mb|
|Price:||Free* [*Free Regsitration Required]|
We will list out some of the scenarios which you may face while using the unit, and explain the cause and solution for the same. We will provide you with the probable cause behind the condition, and also explain the solution for the same. Also, check the working of the timer here, and do the needful corrections. Softener is using more salt for the processing There are high chances that you have altered some salt settings, so do a check on that.
And check the water level in the brine tank here. If more amount of water is present in the tank, activate the flow control of the system, and remove it immediately. Water Pressure has suddenly decreased The probable reason here will be related to the iron buildup within the container. So clean the container properly to remove all kinds of build ups. Getting salt water in the active line Here the cause of the issue will be the plugged injector system, or it may be because of the timer not cycling rightly.
To solve this, you have to simply try to replace the timer. Try cleaning the injector and replace the screen. Iron contents found in the resulting water The only culprit behind this fleck sxt problem will be related to the resin bed.
Keep in mind that maintaining water softener is necessary for long term. A fouled resin bed will let the iron contents to mix well with the processed water. As a solution, you could check all the brine containers, and try increasing the frequency of the regeneration. Also, increase the backwash time in this case. Feel free to ask the problem you are facing with your Fleck unit, by commenting below.
Fleck 3150 Control Valve
Fleck Service Manuals
FLECK 3150 PDF